Connecting a Trench Heater
Sunday, 30 August 2020 | Admin
Connecting a Trench Heater - Questions and Answers
Question - Can I attach a Trench Heater to an Existing Central Heating System?
Answer - Treat a Trench Heater as a Radiator you fit in the floor, you will connect the supply and return pipework as per a normal Radiator.
Question - What Valves do I need tor a Trench Heater?
Answer - You can fit a supply and return lock shield valves and use a remote manifold TRV or controlled valve or fit a TRV at the Trench with a Lock shield as per a standard radiator, the only thing we recommend is using an adjacent wall mounted sensor head if fitting a TRV at the Trench as local heat will impact the TRV otherwise.
Question - If I fit 3 Trench heaters, how do I interconnect them?
Answer - Fit Lock shields to each trench heater, connect them in parallel as per a standard wall mounted radiator and utilise a remote zone control valve if possible.
Question - Can I use any valves for the Trench Heater
Answer - Yes but we recommend using ours so you know they will do the job.